CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. DOMAINE D’APPLICATION. La présente norme énonce les exigences relatives à l’inspection et à la mise à l’essai des réseaux avertisseurs d’incendie et.
|Published (Last):||24 July 2010|
|PDF File Size:||16.46 Mb|
|ePub File Size:||7.1 Mb|
|Price:||Free* [*Free Regsitration Required]|
A brush attachment can ulc s536 04 assist in removing accumulated dust. Check xan date stamp located can ulc s536 04 the back of the detector and ensure you follow the care and maintenance instructions that came with it to make sure to keep it operating at peak efficiency. Building Life Safety Audits. While advances continue to be made in the technology, the need for maintaining proper testing records becomes even more important. Your service agency MUST identify those detectors that it could not perform this test on.
Where hearing impaired patients or occupants are located, it is usual to have strobe lights located along corridors and in individual rooms to indicate an emergency condition exists in the building. Can ulc s536 04 from your hot bath, shower, or operating dishwasher may ulx “set-off” one of these units.
There are two types of smoke detectors alarms: For homeowners with ten year old multi-station type smoke alarms or who may be contemplating changing or upgrading s356 existing units! Smoke can ulc s536 04 fire detectors should be considered an integral part can ulc s536 04 any home or business security system.
The montly test is to ensure that all audible and visual alarm indicators function properly and are loud or visible enough to alert all the occupants to a fire condition. If in doubt, replace the unit and dispose of the old one in a safe manner. These are the units that provide an interconnection to conventionally wired devices like manual pull stations, sprinkler isolation valves, flow switches, low air and the like; If your system employs a UDACT communicator, the technician must ensure that appropriate signals generated by fan system during the testing must be received at the monitoring station; Field addressable relay modules must be listed on the Individual Device Test Recordand their locations and function documented.
This type of detector works best for fast flaming fires that produce small amounts of smoke. A security or fire alarm system that employs integrated smoke detectors is by far the best way to protect your family or workers. Monthly Testing – Requires the building management or designated individual to actually initiate a fire alarm by activating one of the building’s pull stations.
Standards Council of Canada
Most can ulc s536 04 alarm can ulc s536 04 employ zoned annunciators so that fire fighting personnel can be dispatched to the proper area luc the building. These units are vulnerable to electrical failures they won’t function in the absence of power. Fire Safety and Emergency Planning. Supporting field devices must also be listed. Older model alarms may be switching normal household voltage VAC in order to sound an audible alert when a sprinkler head activates. This type of detector is best used in residential applications, as it provides extremely ullc early warning to smoldering type fires that tend give off dense smoke and noxious fumes.
Correction of any troubles should be left in the hands of a trained Anubis Systems Technologies fire alarm service technician. As we noted on the Services page, very few of the service agencies which are engaged in providing annual testing actually perform this to the level required by the Standard.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Extinguishment, Deluge, and Sprinkler Systems. Smoke particles obscure the receiver, and the unit goes into alarm.
Please review additional Article 9 testing requirements on the Passive Systems page. For more information you can can ulc s536 04 us or telephone The function of the various relays correlated to these devices must, however, be individually recorded. A specific reference to the Standard on the front page of the report 5s36.
It’s also prone to false alarms when installed close to bathrooms or kitchens with older style dishwashers. Never paint the sensor!
National Canadian Fire Alarm Code and Standards
Your sprinkler system may incorporate a flow switch or switches that are connected to your smoke ulv. Zones or module numbers 044 the system being tested is addressable must be recorded for each field device on the Individual Device Test Record ; End-of-Line devices resistors – these have to be listed along with their locations on the Individual Device Test Record and specific testing must be conducted that requires their physical dismounting and re-installation; Isolators data buss, power buss, and in-suite ulx isolators – these have to be listed on the Individual Device Test Record including a reference to their actual location and some may require physical dismounting in order to affect a proper test; Smoke detector sensitivity readings – can ulc s536 04 must be recorded on the Individual Device Test Record.
Can ulc s536 04 must be subjected to one of FIVE 5 test methodologies the fifth one involves replacement of the batteries with a new set ; Gen-sets can ulc s536 04 part of s36 emergency power supply must be tested for run and trouble indications at the fire alarm control.
Use only alkaline or lithium type batteries and make sure you double check the expiry date on the battery and test it before you place it in the unit. Daily Testing General – is the responsibility of the building management or an individual they’ve designated to perform these duties. All addressable devices must can ulc s536 04 individually listed on the Device Test Record sheet. Applying household voltage can ulc s536 04 the interconnection wire will result in the destruction of any connected can ulc s536 04 and may even cause a fire.
Fire Alarm System Inspection Services. It’s a good idea to check the battery compartment every six months for leakage or corrosion on the terminals. Annual Testing – The Annual Test of the fire alarm system is performed can ulc s536 04 qualified technical personnel to a specific National Standard. Once a month or so, take your vacuum on it’s lowest setting and utilizing a soft brush attachment, clean out the vents of the detector.
Powered independently of the fire alarm control, these devices are normally not connected to it. Rechargeable batteries shall not be used in smoke alarms unless specifically recommended by the manufacturer.
There are a number of companies in the Lower Mainland that perform this service. Ionization type smoke detectors utilize a small source of radioactive material usually Americium that in fact ionizes airborne particulates and attracts them to to one side or the other of a polarized grid.
If the sensor is part of an actual fire alarm system, make sure you alert other tenants in the building as to what you’re doing as well as your monitoring station if applicable.
Most smoke detectors installed today are wired directly to the household electrical system. The audible signals can consist of bells or buzzers, but can ulc s536 04 some systems, an alarm tone is generated through a series of speakers located on each floor of the premise.
Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber. There is a possibility that you may inadvertently set off the fire alarm system. In some municipalities e.